Izvorni znanstveni članak
Reactor-type tap changers testing
APA 6th Edition
Levi, R., Milojević, G. i Osmanbašić, E. (2017). Reactor-type tap changers testing. Transformers Magazine, 4 (1), 82-88. Preuzeto s https://hrcak.srce.hr/index.php/202379
MLA 8th Edition
Levi, Raka, et al. "Reactor-type tap changers testing." Transformers Magazine, vol. 4, br. 1, 2017, str. 82-88. https://hrcak.srce.hr/index.php/202379. Citirano 07.10.2022.
Chicago 17th Edition
Levi, Raka, Goran Milojević i Edis Osmanbašić. "Reactor-type tap changers testing." Transformers Magazine 4, br. 1 (2017): 82-88. https://hrcak.srce.hr/index.php/202379
Levi, R., Milojević, G., i Osmanbašić, E. (2017). 'Reactor-type tap changers testing', Transformers Magazine, 4(1), str. 82-88. Preuzeto s: https://hrcak.srce.hr/index.php/202379 (Datum pristupa: 07.10.2022.)
Levi R, Milojević G, Osmanbašić E. Reactor-type tap changers testing. Transformers Magazine [Internet]. 2017 [pristupljeno 07.10.2022.];4(1):82-88. Dostupno na: https://hrcak.srce.hr/index.php/202379
R. Levi, G. Milojević i E. Osmanbašić, "Reactor-type tap changers testing", Transformers Magazine, vol.4, br. 1, str. 82-88, 2017. [Online]. Dostupno na: https://hrcak.srce.hr/index.php/202379. [Citirano: 07.10.2022.]
This paper discusses DVtest or Dynamic Resistance Measurement, a new diagnostic method used in detecting on load tap changer (OLTC) operational problems, as applied to reactor-type tap changers. Several cases of tap changer problems are presented, which were detected using the DVtest method – a high speed recording of a DC test current as the OLTC goes from tap to tap. The focus of the article is on the reactor-type tap changers. These reactor OLTC constructions apply Preventive Autotransformers (PA) for current control instead of resistors. Specific features in the current traces due to this particularity are explained. Finally, the article presents a discussion of the principles, DVtest features and defect cases for tap changers in a series transformer/booster arrangement.
Posjeta: 1.437 *